Legionella species colonization of water distribution systems, pools and air conditioning systems in cruise ships and ferries
© Goutziana et al; licensee BioMed Central Ltd. 2008
Received: 10 June 2008
Accepted: 24 November 2008
Published: 24 November 2008
Legionnaires' disease continues to be a public health concern in passenger ships. This study was scheduled in order to investigate Legionella spp. colonization of water distribution systems (WDS), recreational pools, and air-conditioning systems on board ferries and cruise ships in an attempt to identify risk factors for Legionella spp. colonization associated with ship water systems and water characteristics.
Water systems of 21 ferries and 10 cruise ships including WDS, air conditioning systems and pools were investigated for the presence of Legionella spp.
The 133 samples collected from the 10 cruise ships WDS, air conditioning systems and pools were negative for Legionella spp. Of the 21 ferries WDS examined, 14 (66.7%) were legionellae-positive. A total of 276 samples were collected from WDS and air conditioning systems. Legionella spp. was isolated from 37.8% of the hot water samples and 17.5% of the cold water samples. Of the total 96 positive isolates, 87 (90.6%) were L. pneumophila. Legionella spp. colonization was positively associated with ship age. The temperature of the hot water samples was negatively associated with colonization of L. pneumophila serogroup (sg) 1 and that of L. pneumophila sg 2 to 14. Increases in pH ≥7.8 and total plate count ≥400 CFU/L, correlated positively with the counts of L. pneumophila sg 2 to 14 and Legionella spp. respectively. Free chlorine of ≥0.2 mg/L inhibited colonization of Legionella spp.
WDS of ferries can be heavily colonized by Legionella spp. and may present a risk of Legionnaires' disease for passengers and crew members. Guidelines and advising of Legionnaires' disease prevention regarding ferries are needed, in particular for operators and crew members.
It is well documented that cases of Legionnaires' disease (LD) have occurred among passengers of cruise ships and ferries [1, 2]. A World Health Organization compendium published in 2001, showed that from 1970 to 2000, 51 incidents of LD were reported to be associated with ships, involving almost 200 cases, while 10 fatalities were recorded . Since then, repeated reports of outbreaks of LD in passenger ships have been published in the scientific literature [4–6]. In 2006, a total of 11 cases of ship associated LD were reported to the European Working Group for Legionella Infections . From November 2003 through May 2004, eight cases of LD among persons who had recently travelled on cruise ships were reported to the United States Centres for Diseases Control and Prevention . Water distribution systems  and whirlpool spas [6, 10] of passenger ships have been identified as the source of infection, while a possible link with air-conditioning systems have also been documented .
About 30 million passengers are transferred every year by ferries from continental Greece, to the islands. Furthermore, many cruise ships sailing in the Mediterranean Sea include in their itineraries, Greek ports destinations. In 2004, a Belgian passenger travelling by ship from Greece to Italy developed LD , while two cases were associated with ferries in 1994 and 1997. However, both patients were exposed to other likely sources of infection (hotels) and no ferries were investigated microbiologically . Few data exists regarding the prevalence of Legionella spp. contamination, and the factors that contribute to Legionella spp. colonization of water systems in passenger ships, and even fewer data exists for ferries.
The aim of this study was to investigate Legionella spp. colonization of water distribution systems (WDS), recreational pools, and air-conditioning systems aboard ferries and cruise ships and to identify risk factors for Legionella spp. colonization associated with ship water systems and water characteristics.
From May through July 2004, 269 samples were collected from hot (172 samples) and cold (97 samples) WDS and 7 samples from air conditioning systems of 21 ferries berthed at harbours in Greece. Moreover, 123 samples were collected from hot (103 samples) and cold (20 samples) WDS, 2 samples from air conditioning systems and 8 samples from spa pools of the 10 cruise ships that acted as floating hotels at the Piraeus harbour during the Olympic Games in August 2004. The sample collection and microbiological analysis were part of the Environmental Health Surveillance Program developed by the Olympic Planning Unit and implemented for the Athens 2004 Olympic Games, which is described elsewhere . The sampling was conducted by the Public Health Officers of the Prefecture Public Health Department of Piraeus in cooperation with the National School of Public Health personnel.
In order to obtain a representative sample of each ship WDS, 4 to 20 samples were collected from selected predetermined points, while the total number of samples was based on the total number of cabins and number of decks. The sampling points were chosen according to the EWGLI guidelines  a) in the engine room, the hot water leaving the water heater, and when possible the circulating hot water returning to the heater, b) the outlet nearest to the entry of the hot water into the ship WDS, and the most distal site within the WDS, c) showers or taps of crew members or passenger cabins on different decks to be representative of the different loops of the WDS. Four samples were collected from each cabin: One sample was collected from hot water discharging from the shower head immediately after it was turned on (immediate sample) and the second after 60 seconds flow time (post flush sample). Another sample was collected from cold water discharging from the tap immediately after it was turned on and the fourth after two minutes flow time . The microbiological test results of the samples (immediate and "post flush sample") collected from each point (tap or shower head) was considered as a unique result, to characterise the sampling point as contaminated and thereafter in the assessment of the need for remedial actions according to the EWGLI criteria.
Two samples were collected from each swimming or spa pool. In addition, samples collected from the condensate sumps and their drainage arrangements of the ship air conditioning system.
A standardized form was completed during the sampling including details on: sampling point (cabin, fan room, pool), sample temperature, free chlorine, and pH. The temperatures were measured using a calibrated thermometer, placed in the middle of the water stream. Free chlorine and pH were measured using a portable, microprocessor-based meter HANNA HI93710. Samples were collected in 0.5 litre sterile containers containing sufficient sodium thiosulphate to neutralize any chlorine or other oxidizing biocides.
Water samples were tested for Legionella spp. using methods in accordance with ISO 11731 , and for aerobic count at 37°C for a minimum of 48 h incubation using the pour-plate method according to ISO 6222 . Microbiologic analysis for Legionella spp. was performed by the National Legionella Reference Laboratory of Southern Greece in Athens. The detection limit of Legionella was ≥500 CFU/L. Before and during the research period, the reference laboratory participated in an external quality-control scheme for Legionella spp. detection in water (Quality Management Ltd, Lancashire, UK), through a periodic distribution of the water samples seeded with unknown Legionella spp. and concentration. The total microbial counts at 37°C for 48 h were obtained twice by the pour-plate method on yeast extract agar (LAB M). Methods used for the microbiological analysis have been described elsewhere .
Thermal disinfection was carried out by raising the temperature of the hot water storage tank content to 70–80°C and then circulating this water throughout the system for up to three days. The temperature at the hot water storage tank was raised high enough to ensure that the temperatures at the taps and appliances would not have fallen below 65°C. Each tap and appliance was run sequentially for at least five minutes at the full temperature, and the temperature was measured. The standardized disinfection guidelines were printed and distributed to the persons responsible for the buildings by the Prefecture Departments of Public Health personnel. Hoteliers or the hospital staff applied the disinfection procedure, and when possible supervised by the Prefecture Departments of Public Health personnel .
A detailed standardized questionnaire was developed to record information about the ship water supply systems, which was used to evaluate risk factors, possibly associated with Legionella spp. colonization and included information on: 1) the ship characteristics: ship name, unique code, type of ship, owner, itinerary, net tonnage, gross tonnage, ship age, passenger and crew member capacity, 2) the water distribution system components: type of water source (onshore bunkered, evaporator, reverse osmosis), number of water tanks, and presence of water treatment system including its characteristics (disinfection, filtration, softening), 3) the water distribution system characteristics: plumbing material, water tank material, and thermal insulation of the system, and, 4) the heating system, presence of a hot water tank and its volume, and characteristics of water recirculation systems. Water operating temperature and the last date of disinfection was also recorded.
Data were analyzed with Epi-Info 2000 (CDC, Atlanta, GA, USA) and SPSS for Windows Release 11.0.1 software (SPSS Inc, Chicago, IL, USA). Chi square test or Fisher exact test were used for analyzing qualitative data, while t test or Mann-Whitney test were used for quantitative data. Relative risk (RR) and 95% confidence interval (CI) were calculated to assess categorical risk variables associated with legionellae-positive test results. Results were considered statistically significant when the P value was <0.05.
No sample collected from the cruise ships was positive for Legionella spp.
Hot WDS of 14 ferries (66.7%) showed a Legionella spp. count ≥500 CFU/L in at least one sample. Hot WDS of 13 ferries (61.9%) fulfilled the criteria of the European Surveillance Scheme for Travel Associated Legionnaires' Disease guidelines (EWGLI)  for taking remedial actions: at least one sample with bacteria count ≥104 CFU/L, or more than two samples with bacteria count >103 but <104 CFU/L. These ferries required remedial actions according to the EWGLI. A total of 7 ferries WDS were contaminated with concentrations of ≥104 CFU/L in at least one sample, whereas 4 of 7 ferries were colonized with ≥105 CFU/L in at least one sample. Out of the 13 WDS disinfected, 5 (38.5%) needed second disinfection application and two (15.4%) needed third.
Legionella spp. colonization of hot and cold water samples examined from ferries water distribution systems
No. of samples/total (%)
L. pneumophila serogroup 1
L. pneumophila serogroups 2–14
Legionella non pneumophila
Hot water samples
No. of positive samples/total (%)
No. of samples with 500–999 CFU/L/total (%)
No. of samples with 103-9999 CFU/L/total (%)
No. of samples with ≥ 104 CFU/L/total (%)
Cold water samples
No. of positive samples/total (%)
No. of samples with 500–999 CFU/L/total (%)
No. of samples with 103-9999 CFU/L/total (%)
No. of samples with ≥ 104 CFU/L/total (%)
Out of the 97 cold water samples examined, 17 (17.5%) were positive, 7 samples had concentrations between 103-9999 CFU/L and 1 sample was heavily colonized with colony counts ≥104 CFU/L (Table 1).
A statistically significant lower water temperature (P = 0.0004) was found in ferries hot water samples [median = 50°C (Interquartile range, IQR = 41.60–55.95)] in comparison to the temperatures found in cruise ships [median = 53.5°C (IQR = 50.00–56.80)]. The median temperature of ferries cold water samples was 23°C (IQR = 20.30–26.00).
Association of physical, chemical, and microbiological water characteristics with Legionella spp. concentration of hot and cold water samples on ferries water distribution systems
No of positive samples for Legionellaspp.
pH ≥7.8 (%)
pH <7.8 (%)
≥ 55°C (%)
< 55°C (%)
L. pneumophila sg 1
L. pneumophila sg 2–14
Legionella non pneumophila
Total plate count
≥ 0.2 mg/L (%)
< 0.2 mg/L (%)
≥400 CFU/L (%)
<400 CFU/L (%)
L. pneumophila sg 1
L. pneumophila sg 2–14
Legionella non pneumophila
Out of the 101 immediate samples examined, 41 (40.6%) were positive for Legionella spp. while, out of the 168 post flush samples examined, 41 (24.4%) were positive (RR = 1.66, CI = 1.17–2.37, P = 0.007). In addition, out of the 139 samples collected from the most distal sites within the WDS, 48 (34.5%) were positive for Legionella spp. and out of the 30 samples collected from the outlet nearest to the entry of the hot water into the ship WDS, 15 (50%) were positive for Legionella spp. (RR = 1.44, CI = 0.94–2.21, P = 0.08).
Our data indicate that at the time of the study, 66.7% of the water distribution systems of ferries were positive for Legionella spp. with concentrations of ≥500 CFU/L in at least one sample and 33.3% were heavily colonized. Extremely high concentrations (>3 × 105 CFU/L) were found in one ferry and specifically in samples collected from the third class cabins with common showers that were rarely used by passengers. According to the European Surveillance Scheme for Travel Associated Legionnaires' Disease guidelines  concerning action levels following Legionella sampling in hot and cold water systems, 13 ferries hot water distribution systems (61.9%) needed remedial actions and thermal disinfection was applied. About 38% of the WDS disinfected needed second disinfection application and 15% needed third. This shows that thermal disinfection is not totally effective in eradicating Legionella spp. Similar were the findings of a previous study conducted in WDS of buildings (hotels, hospitals etc.) .
A similar prevalence study was carried out on 2 cruise ships and 7 ferries docked at the seaports of northern Sardinia in 2004, indicated that 6/7 ferries were positive, 42% (38/90) of the water samples examined were contaminated by Legionella spp. and 77.8% of the water samples contained ≥104 CFU/L . In 1993, a survey carried out in 33 water tanks of yachts in Athens showed that approximately 40% of them were positive for Legionella spp. . In our study, we observed a lower frequency of L. pneumophila sg 1 (in 43 samples), while 87 of the total 96 isolates from the cold and hot water samples were L. pneumophila. In the study carried out in the northern Sardinia, no sample contained L. pneumophila sg 1, however L. pneumophila was isolated in 42/44 samples (95.5%), followed by L. micdadei (4.5%). The strains that were identified in that particular study were L. pneumophila sg 6 (45.2%; 19 samples), sg 2 to 14 (42.9%), sg 5 (7.1%) and sg 3 (4.8%) .
We observed high colonization (17.5%) of Legionella spp. in the cold WDS, compared to the contamination of other buildings such as hotels, where only 6.4% of the cold samples were positive . This may be attributed to the relatively high temperature (median = 23°C, IQR = 20.30–26.00) of cold water aboard ferries. Pipes of cold water pass through the high temperature engine rooms of the ships. Controlling the water temperature in order to prevent Legionella spp. colonization of WDS will be effective only if pipes are insulated. Cold water should be maintained at temperatures below . Where this temperature cannot be achieved due to local conditions, suitable alternative residual disinfection procedures must be used and supported by regular (at least quarterly) testing for legionellae .
In a previous study aboard 2 cruise ships no water system including potable water distribution system, spa or swimming pool, was positive for Legionella spp. . In our study, the relatively high temperature of hot water aboard cruise ships in comparison to the temperatures found in ferries, may partially explain the great difference in Legionella spp. colonization between cruise ships and ferries. In addition, the ten cruise ships that were investigated applied the requirements of the United States Vessel Sanitation Program Manual (VSP) regarding potable water safety and swimming and spa pool management. The legionellae-negative microbiological results of the samples collected from the cruise ships indicate that correct compliance with the requirements that were included in the VSP manual were effective to maintain legionellae-free water systems. These guidelines involve continuous halogenation to at least 2.0 mg/L free residual halogen at the time of bunkering or production of potable water, maintenance of a free residual halogen concentration of ≥0.2 mg/L and ≤5.0 mg/L throughout the distribution system and periodical disinfection of the distribution system and water tanks, and other control measures regarding spa pools . Other additional measures may have been applied aboard the cruise ships.
No significant association was found between L. pneumophila sg 1 concentrations and free chlorine concentration of ≥0.2 mg/L. Contrary, free chlorine of ≥0.2 mg/L inhibited colonization of L. pneumophila sg 2–14, Legionella non pneumophila and Legionella spp. These findings may imply that L. pneumophila sg 1 is more resistant in higher chlorine concentrations. This was also observed in a another study in hotels .
The high levels of Legionella spp. and the high number of positive samples for L. pneumophila found aboard ferries, present a risk for infection, since most ship associated cases have been ascribed to infection by L. pneumophila sg 1 . However, L. pneumophila sg 5 [5, 6], 3, 4, and L. longbeachae sg 1  have been isolated from clinical specimens of passengers with LD. Unfortunately, we did not monitor the development of pneumonia symptoms among passengers and crew members during the study period. Practical difficulties such as the short stay period aboard ferries ranging from a few hours to one day maximum, limits the evidence for linking the source of infection. In addition, many of the passengers are travelling and may be exposed to legionellae in other locales as they travel (e.g., hotels, restaurants, etc.). However, the limited stay period aboard ferries limits the risk of infection.
Since water systems of ferries could be a possible source for infection, during LD case investigation, exposure history should include information on travelling by ships. This will help to identify passenger cases that usually go undetected, to timely implement environmental control measures and to prevent possible future outbreaks in subsequent voyages.
The temperatures of the hot water samples were negatively associated with contamination with L. pneumophila sg 1 and with sg 2 to 14. Similar were the findings of a previous study in hotels WDS . In our study, increases in pH correlated positively with the counts of L. pneumophila serogroups 2 to 14. These findings confirm other reports, which indicated a positive association of L. pneumophila with pH .
The limited number of legionellae-positive WDS of ferries (only 14 positive of the total 21 examined), influence the results of association between colonization and ship factors such as capacity and number of passengers, and therefore we could not draw any conclusions.
LD outbreaks have occurred aboard passenger ships in recent years [8, 22], and even fatal cases have been reported . In many cases the source of the organism was clearly demonstrated [9, 10]to be the ship's water system. LD outbreaks cause negative economic impact on the cruise ship industry and may result in removing a vessel from service, or delay the sailing from a port to allow control measures to be carried out . Three ships are known to have changed owners and names after being linked with cases of legionellosis . During 2004, there were 205 cruise ships with itineraries in Europe, which represents 87% of all cruise ships in operation http://www.europeancruisecouncil.com/faq.html. Measures for the prevention and control of the disease should be further taken to a European or even to an International level. In 2005, the European Commission funded the SHIPSAN project which aims at assessing the usefulness of an EU ship sanitation program and coordinated action for the control of communicable diseases in cruise ships and ferries http://www.eu-shipsan.gr/. We believe that a future European ship sanitation program should include LD prevention and control guidelines.
Apart from the EWGLI guidelines which apply in accommodation sites in general, specific measures for passenger ships have been published by the WHO in the revised draft for review of the Guide to Ship Sanitation and in the book entitled "Legionella and the prevention of Legionellosis" . CDC published recommendations to minimize transmission of Legionnaires' disease from whirlpool spas on cruise ship in 1997 .
This study demonstrates that water distribution systems of ferries can be colonized by Legionella spp. and present a possible risk for Legionnaires' disease. Both hot and cold water distribution systems can be colonized. Chemical treatment and monitoring of drinking water quality including halogen disinfection, pH adjustment, and water temperature control in hot water systems are recommended as control measures aboard ferries. Older ferries are of higher risk. During LD case investigation, patient history should record any exposure to recent travel by ships. Guidelines and advising of Legionnaires' disease prevention to ferries operators and crew members are needed.
This work was funded by the Hellenic Ministry of Health. We extend thanks to the staff of the National School of Public Health. We also thank Prof. Alkiviadi Vatopoulo, Dr. Emmanuel Velonaki, Dr Vasilios D. Daniilidi, Mrs L. Georgiadou, Mr George Panagako, Mr. Christo Maglara, Mr. Argiri Kasdnesti, Mrs Dimitra Markea and Mr. Christo Soldato. We wish to thank all the masters and crews of ships for their co-operation in the surveys.
- Minooee A, Rickman LS: Infectious diseases on cruise ships. Clin Infect Dis. 1999, 29: 737-743. 10.1086/520426.View ArticlePubMedGoogle Scholar
- Rowbotham TJ: Legionellosis associated with ships: 1977 to 1997. Commun Dis Public Health. 1998, 1: 146-151.PubMedGoogle Scholar
- WHO: Sustainable Development and Healthy Environments. Sanitation on ships: compendium of outbreaks of foodborne and waterborne disease and Legionnaire's disease associated with ships. 1970, –2000Google Scholar
- Beyrer K, Lai S, Dreesman J, Lee JV, Joseph C, Harrison T, Surman-Lee S, Luck C, Brodhun B, Buchholz U, Windorfer A: Legionnaires' disease outbreak associated with a cruise liner, August 2003: epidemiological and microbiological findings. Epidemiol Infect. 2007, 135 (5): 802-810. 10.1017/S0950268806007473.View ArticlePubMedGoogle Scholar
- Kobayashi A, Yamamoto Y, Chou S, Hashimoto S: Severe Legionella pneumophila pneumonia associated with the public bath on a cruise ship in Japan. J Anesth. 2004, 18: 129-131. 10.1007/s00540-003-0218-0.View ArticlePubMedGoogle Scholar
- Kura F, Amemura-Maekawa J, Yagita K, Endo T, Ikeno M, Tsuji H, Taguchi M, Kobayashi K, Ishii E, Watanabe H: Outbreak of Legionnaires' disease on a cruise ship linked to spa-bath filter stones contaminated with Legionella pneumophila serogroup 5. Epidemiol Infect. 2006, 134: 385-391. 10.1017/S095026880500508X.View ArticlePubMedGoogle Scholar
- EWGLI: European Guidelines for Control and Prevention of Travel Associated Legionnaires' Disease. 2005Google Scholar
- Anon: Cruise-ship – associated Legionnaires disease, November 2003–May 2004. MMWR Morb Mortal Wkly Rep. 2005, 54: 1153-1155.Google Scholar
- Castellani Pastoris M, Lo Monaco R, Goldoni P, Mentore B, Balestra G, Ciceroni L, Visca P: Legionnaires' disease on a cruise ship linked to the water supply system: clinical and public health implications. Clin Infect Dis. 1999, 28: 33-38. 10.1086/515083.View ArticlePubMedGoogle Scholar
- Jernigan DB, Hofmann J, Cetron MS, Genese CA, Nuorti JP, Fields BS, Benson RF, Carter RJ, Edelstein PH, Guerrero IC, Paul SM, Lipman HB, Breiman R: Outbreak of Legionnaires' disease among cruise ship passengers exposed to a contaminated whirlpool spa. Lancet. 1996, 347: 494-499. 10.1016/S0140-6736(96)91137-X.View ArticlePubMedGoogle Scholar
- Joseph CA, Hutchinson EJ, Dedman D, Birtles RJ, Watson JM, Bartlett CL: Legionnaires' disease surveillance: England and Wales 1994. Commun Dis Rep CDR Rev. 1995, 5: R180-R183.PubMedGoogle Scholar
- Hadjichristodoulou C, Mouchtouri V, Vaitsi V, Kapoula C, Vousoureli A, Kalivitis I, Chervoni J, Papastergiou P, Vasilogiannakopoulos A, Daniilidis VD, Kremastinou J: Management of environmental health issues for the 2004 Athens Olympic Games: is enhanced integrated environmental health surveillance needed in every day routine operation?. BMC Public Health. 2006, 6: 306-10.1186/1471-2458-6-306.View ArticlePubMedPubMed CentralGoogle Scholar
- ISO: ISO 11731. Water Quality – detection and enumeration of Legionella. Part 1. ISO. 1998Google Scholar
- ISO: ISO 6222. Water Quality – Enumeration of culturable micro-organisms – colony count by inoculation in a nutrient agar culture medium, 1999. ISO. 1999Google Scholar
- Hadjichristodoulou C, Goutziana G, Mouchtouri V, Kapoula C, Konstantinidis A, Velonakis E, Vatopoulos A, Kremastinou J: Evaluation of standardized scored inspections for Legionnaires' disease prevention, during the Athens 2004 Olympics. Epidemiol Infect. 2006, 134: 1074-1081. 10.1017/S0950268806006042.View ArticlePubMedPubMed CentralGoogle Scholar
- Mouchtouri V, Velonakis E, Hadjichristodoulou C: Thermal disinfection of hotels, hospitals, and athletic venues hot water distribution systems contaminated by Legionella species. Am J Infect Control. 2007, 35: 623-627. 10.1016/j.ajic.2007.01.002.View ArticlePubMedGoogle Scholar
- Azara A, Piana A, Sotgiu G, Dettori M, Deriu MG, Masia MD, Are BM, Muresu E: Prevalence study of Legionella spp. contamination in ferries and cruise ships. BMC Public Health. 2006, 6: 100-10.1186/1471-2458-6-100.View ArticlePubMedPubMed CentralGoogle Scholar
- Wewalka G, Gruner I: Legionellae in water tanks of yachts. Proceedings of the 9th Meeting of the European Working Group on Legionella Infections. Viterbo, Italy, EWGLI, 69-71.
- Mouchtouri V, Velonakis E, Tsakalof A, Kapoula C, Goutziana G, Vatopoulos A, Kremastinou J, Hadjichristodoulou C: Risk factors for contamination of hotel water distribution systems by Legionella species. Appl Environ Microbiol. 2007, 73: 1489-1492. 10.1128/AEM.02191-06.View ArticlePubMedPubMed CentralGoogle Scholar
- Centres for Disease Control and Prevention NCfEH: Vessel Sanitation Program Operations Manual. 2005, Atlanta: US Department of Health and Hunam Services, Public Health Service, Centres for Disease Control and PreventionGoogle Scholar
- Borella P, Montagna MT, Stampi S, Stancanelli G, Romano-Spica V, Triassi M, Marchesi I, Bargellini A, Tato D, Napoli C, Zanetti F, Leoni E, Moro M, Scaltriti S, Ribera D'Alcala G, Santarpia R, Boccia S: Legionella contamination in hot water of Italian hotels. Appl Environ Microbiol. 2005, 71: 5805-5813. 10.1128/AEM.71.10.5805-5813.2005.View ArticlePubMedPubMed CentralGoogle Scholar
- Ricketts KD, Joseph CA: Legionnaires' disease in Europe 2003–2004. Euro Surveill. 2005, 10: 256-259.PubMedGoogle Scholar
- WHO: Legionella and the prevention of Legionellosis. World Health Organization. 2007Google Scholar
- CDC: Final recommendation to minimize transmission of Legionnaires' disease from Whirlpool Spas on cruise ship. 1997, Atlanta, Georgia: CDCGoogle Scholar
- The pre-publication history for this paper can be accessed here:http://www.biomedcentral.com/1471-2458/8/390/prepub